We provide services to companies that demand the highest quality. We work for the best results, so we are proud of our customers’ feedback on the work done.
UAB ,,Biržų duona“, legal entity’s code 154838481, located in Plento g. 6, LT-41128 Biržai purchased energy audit service from UAB „Energy Advice“. We acknowledge that UAB „Energy Advice“ performed energy audit was comprehensive. Recommendations for reducing transport fuel consumption, optimal renewable energy source integration and operation, reducing heating generation losses, an increase of electrical network reliability, and installation of an analytical information system were provided. UAB „Energy Advice” specialists presented results and answered questions regarding our concerns.
Multimeda is one of the biggest solid wood furniture manufacturers in Lithuania. In our production facilities we use dust collection systems with a total installed capacity of over 350 kW. These systems contribute significantly to our energy consumption, therefore, we ordered Energy Advice services to find energy mitigation opportunities. Energy Advice team applied EA-SAS software, created digital model of dust collection systems in our factory and calculated energy saving potential. The main finding was that due to big cross section area of main ducts, air flow speed can be too small to transport heavier dusts, therefore fans’ speed control cannot be done with existing ducts design. However, EA-SAS calculations also showed that by selecting optimal cross section area of ducts it is possible to ensure required air speed even with reduced fans’ speed. This would allow to save over 15% from dust collection system’s energy consumption. Therefore, we recommend EA-SAS Ventilation program for other companies that face problems with dust collection systems.
We confirm that Energy Advice has developed a Digital Twin for the glass melting furnace. Energy Advice has installed EA-SAS software, developed a mathematical model of the glass melting furnace, and commissioned it. Digital Twin model allows us to monitor glass furnace process remotely, also as control technological process in real time by providing optimum operation setpoints. Project benefits: reduced energy consumption for glass melting process, increased glass furnace life time, identified furnace maloperation, determined components efficiency. The project was implemented on time. We recommend Energy Advice as reliable partner for Digital Twin development and implementation.
UAB “Šalčininkų šilumos tinklai” confirms that UAB “Energy Advice” has carried out a digitization project for a biofuel boiler house (5 MW). EA-SAS Boiler system monitors, analyzes and evaluates the efficiency of the boiler and perform automated control in order to increase production efficiency. The implemented solution helps to burn fuel more efficiently, the boiler NVK has been improved. We managed to prolong time between maintenance due to data analysis. We recommend UAB “Energy Advice” as a reliable partner in digitization projects.
UAB “Šalčininkų šilumos tinklai” is a district heating company and supply ~18,5 GWh heat per year. We have been using UAB “Energy Advice” solution EA-SAS Heating based on Digital Twin technology from 2020. Thermo-hydraulic calculations and real time date evaluation is performed constantly in order to control the network and reduce losses. The digital model of the heating network also allows us to make fast and high-quality network development decisions. We confirm that even small town heat supply companies benefit from digitization projects, and we recommend Energy Advice as a reliable partner in digitization and energy saving.
Vilnius city municipality together with Energy Advice joined an Intelligent Energy lab initiative. The purpose of this initiative is to create open platform for generating and implementing smart energy solutions for Vilnius city. For Intelligent Energy lab initiative, Vilnius city municipality building at Konstitucijos av. 3 was selected for increasing energy efficiency with the help of state-of-the-art digitalization methods. Energy Advice used EA-SAS analytical system to read smart metering data and create digital twin model for building in Konstitucijos pr. 3. Digital twin allowed to determine reasonably and wastefully consumed thermal, cooling, electrical energy and water amount for each operation hour. During the project, Dashboard window with reports was created at EA-SAS program that allows to easily track energy consumption indexes and promptly respond for the responsible personnel. During the project it was determined that the potential to reduce energy consumption can reach 30%. Services were provided with great efficiency and quality. We recommend cooperation with UAB „Energy Advice“.
AB Rokiškio sūris is one of the largest manufacturer of the dairy products in Lithuania. In order to produce a high quality product, an energy-intensive cooling and refrigeration process is necessary. In pursuit to reduce electrical energy consumption in refrigeration systems it was decided to implement Digital Twin. Data from smart-metering and Scada is collected and analyzed in the real time at one EA-SAS platform. Set points for Refrigeration compressors operation are calculated at EA-SAS Cooling and sent to refrigeration control system automatically without human interaction. Project allowed to reduce the refrigeration system electricity consumption, it lets us to monitor the compressor room operation remotely and to know the system’s COP in real time, thus allowing to make maintenance decisions.
AB Rokiškio sūris confirms that the company UAB Energy Advice provides the service of maintenance and control of energy consumption indicators. Based on planned hourly production volumes, the EA-SAS program forecasts energy consumption volumes for each hour. The system provides recommendations on how to reduce energy consumption and operate the equipment properly. Energy Advice specialists also provide high-quality consultations on electricity purchase issues: based on the company’s energy consumption and electricity price forecasts, it helps to choose the most favorable electricity purchase plan.
UAB „Šakių šilumos tinklai“ (Šakiai District Heating) has been using UAB Energy Advice digitalisation services since 2019. With a platform EA-SAS Heating a digital twin of existing district heating network was created. Digital district heating network management allowed us to move to low supply temperature operation. Now we can efficiently plan network expansion and maintenance; all our information is accessible remotely through web browser. Our experience shows that Energy Advice is a trustworthy partner providing quality services and supporting our company in reaching digitalisation and energy saving goals.
AB Rokiškio sūris states that company UAB Energy Advice provides control of energy consumption indexes. Based on hourly production volumes EA-SAS software forecasts energy consumption for each hour. System provides recommendations on how to reduce energy consumption and operate devices properly. What is more, Energy Advice specialists provides professional consulting regarding electricity procurement: helps to choose the most advantageous electricity procurement plan, based on company electricity consumption and electricity price forecasts.
AB Grigeo states that company UAB Energy Advice have implemented EA-SAS Boiler analytical system for 18 MW Biomass Boiler with economizer operation control. During this project, Data Collector software was installed for real time data collection from Boiler control system. Biomass Boiler Digital Twin (mathematical model) that fully describes biomass combustion, heat exchange and energy flows was implemented. Overall energy balance was structured and is calculated for each 5 minutes. After implementing this project, amount of biomass fuel is recorded every 5 minutes, biomass fuel calorific value and moisture content are calculated in real-time. Optimal Control algorithm was developed. EA-SAS Boiler system provides optimal Biomass fuel and Primary and Secondary air control tasks (Set Points) for each minute. This optimal control tasks service helps Company’s operators increase efficiency of biomass combustion. Implementation of this project increased Biomass Boiler efficiency and helped to reach pursued energy production efficiency goals.
We note that Energy Advice specialists have smoothly implemented analytical system EA-SAS Boiler and provided high quality consulting on increasing Biomass Boiler efficiency.
With this recommendation we confirm that UAB Šakių šilumos tinklai are using services and IT tools EA-SAS and EA-PSM Hydraulic provided by Energy Advice. Company specialists hace sucessfully completed network digitalization tasks: real-time optimal network control and hydraulic network modelling, optimization of pipelines diameters. Our company experience shows that Energy Advice is a reliable partner that provides services in great quality and helps our company to achieve digitalization and energy efficiency goals.
AB KLAIPĖDOS MEDIENA is one of the largest companies of the VMG Group in Lithuania. We are producers of particle board and cabinet furniture from finished PB.
In order to improve efficiency of manufacturing processes, we have chosen company UAB “Energy Advice” to conduct full-scale energy audit and make detail evaluation of compressed air and ventilation system. Energy Advice professionals proposed solutions for energy efficiency improvement. In the report, technical methods are proposed on how to reduce energy consumption of dust collection, compressed air, electricity distribution and heating systems. Services were provided on time and with great quality. We recommend Energy Advice as a reliable partner.
Viking Malt is the leading malting company in Nothern Europe. We state that company Energy Advice performed energy and IT audit and highlighted energy intensive processes and biggest saving opportunities. Later analytical system EA-SAS was installed for production process digitalization and optimization. Now we have all Data in one place and use it for decision making. Also, we have a digital twin of the production plant technological process including grain steeping, germination and drying processes. Digital twin technology provides optimal control set points that allows us tp improve technological process characteristics and energy efficiency. We recommend Energy Advice as a reliable partner.
Electrum sp. z.o.o. engineers are using software EA-PSM by company Energy Advice. We use software to work with the most challenging renewable energy projects, also industrial and distribution networks. EA-PSM functionalities cover majority of our needs for electrical network calculations. We are pleased with Energy Advice consulting and support that includes new functionalities development according to our project requirements.
UAB Vilniaus energija engineers are using software EA-PSM that allows to make fast, reliable and economically feasible decisions on optimizing electrical network. It helps us to reduce power losses and increase network reliability. We rely on Energy Advice team because we always receive clear and useful responses to our problems.
EA-PSM is user-friendly and easy to use tool with trusted output data and calculations. During the training I understood how to analyse company’s electrical grid, control losses and find inexpensive and reliable solutions which help to ensure the durability of equipment. Engineers are very helpful and responsive.
UAB Axis Power acquired a license of the EA-PSM software. It helps us to solve the challenges of implementing projects. An advantage of EA-PSM – all functions in one program. It is a reliable, time-saving tool for engineers. The program EA-PSM performs tasks such as electrical equipment selection and verification of existing schemes items under load currents and short-circuit conditions; selection of capacitor banks and reactive power balancing; current and voltage harmonic levels of network distribution and electromagnetic compatibility assessment; relay protection and automatic provisions calculation and coordination. UAB Axis Power recommends software EA-PSM. We especially appreciate fast and high quality services and professional advice.
JSC “Energy Advice” conducted audit on “Grigeo” 6kV SI-2 substation reconstruction technical project (electric design and relay protect parts). During a short period of time, “Energy Advice” team professionally evaluated technical design solutions compatibility with local and international standards. High design project quality was reached, as a result of this study. We recommend JSC “Energy Advice” as trusty partner which carries a high level of service.
“EA-PSM” helps our engineers solve challenging tasks, calculate parameters and choose the required equipment for PV systems to be efficient and reliable. “EA-PSM” software has a user friendly interface and innovative solutions to prepare reports. Also, the company’s team is always ready to assist us in our daily use of the software. “UAB DETRA Solar” recommends “Energy Advice” as trusted partner.
We started using EA-PSM software for carrying out various studies like power flow analysis, short circuit analysis, harmonic analysis and arc flash analysis as a part of our design process for our clients and fidn it extremely useful. The software is simple and easy to handle, thus enabling our design team get acquainted with the software quickly, saving the time involved. This also enabled enhancing the confidence of the team in their design activities. We would be happy to recommend to our fellow consultants to liberally use this software that would ascertain the reliability of the design and the confidence level of the designer engineers.
In 2016 company JSC Energy Advice accomplished detailed audit of Lithuania’s central bank building systems (Gedimino pr. 6, Totorių str. 2, 4 and Žirmūnų str. 151, Vilnius). Audit included comprehensive analysis of electrical, heating and air conditioning systems. Provided results consist of full electrical network one-line diagrams, analysis of heating, hot water and air conditioning systems condition, calculation of reliability factors and probabilities of uninterruptible power supply failure for first category electrical loads. Proposed electrical and heating networks optimization techniques and recommended solutions for problems are sufficiently justified and explained.
We are one of the engineering service providers acclaimed by clients like FORD INDIA, SAINT GOBAIN GLASS, GE ENERGY, DOW CHEMICALS, APOLLO TYRES, SP INFO CITY, SIEMENS LTD, ETC for the technical competency in electrical design, project engineering, consultancy, management and services. We are offering comple complete power system analysis, protection coordination study, reengineering industrial electrical distribution system, predictive maitenence services and risk analysis etc and offer complete solution for safe working environment. We find EA PSM software a versitile tool to design & implement new projects to international standards, select protection system components, apply better relay coordination settings, scrutinise the existing power disribution arrangements and apply corrective measures, predictive maitenence scheduling, safety measures etc.
AB „Kauno energija” (Lithuania, EU) is the centralized heat supplier for the residents and organizations of Kaunas town and Kaunas district for more than 50 years. As of today, AB „Kauno energija” is highly developed modern DH Sector, the second largest utility in Lithuania according to the business volumes. The heat is being supplied to over 117 thousand consumers (households and organizations), which takes approximately 20 percent of country’s centralized heat supply market. UAB Kaunas energy is using software EA- PSM. This program is best for recognition of unforeseen errors when acquiring new equipment. Working with this software we can select optimal parameters for motors, generators, cables, capacitors, transformer, frequency drives, etc. Existing equipment failure analysis and prevention from the disturbances are performed to increase network reliability. The program is also used for the power flow, short circuit calculations, harmonic load flow as well as solving the relay protection and automation coordination tasks. We confirm that EA- PSM implemented by Energy Advice fulfilled all expectation of AB „Kauno energija”.
Public Company “ORLEN Lietuva” ordered and “Energy Advice” has conducted the “ORLEN Lietuva” personnel training program for electrical engineers to update the existing professional knowledge. “Energy Advice” can be described as professional and efficient supplier since the quality of training always meets the expectations of the Company’s management. We recommend “Energy Advice” as a qualified supplier.
„Kauno baldai“, company code 133513698, registered in Drobes str. 66 LT-45500, Kaunas purchased JSC „Energy Advice“ energy consumption audit. We note that the JSC „Energy advice“ audit was done thoroughly: engineers analyzed the compressed air and air draught systems as well as electricity, heating and water consumption. The company provided recommendations on savings and solutions to optimize electricity, water, compressed air and heating costs. The experts presented the results and answered our questions.
JSC “Energy Advice” team found saving opportunities on the most energy intense systems like ventilation and compressed air. They have calculated savings potential by the implementation of the solar power plant and building insulation. Due to the recommendations, we have avoided expenditures on less efficient saving opportunities and can concentrate on the cost-effective solutions. We recommend Energy Advice audit services.
JSC “Energy Advice” implemented Energy Audit services according to Directive 2012/27/ES in JSC “Kitron”. Experienced energy consultants identified saving opportunities in heating, humidification and cooling systems. Also, provided recommendations for energy efficient operation of the ventilation system. We highly recommend Energy Advice to companies that are seeking to reduce their energy consumption.
A company JSC “IOCO Packaging”, company code 110564826, registered at Pusaloto str. 212, Panevezys, bought energy consumption audit service from JSC “Energy Advice”. Detail energy audit services accomplished comprehensively: analysed compressed air systems, gas, electricity and heat consumption. Energy audit report, ensured successful EU funding in “Renewable energy sources for industry LT+” program.
Energy Advice auditors performed energy efficiency audit in our company, found energy consumption of the most energy intensive manufacturing processes and for separate product groups, because of this, now we can calculate separate products prime cost with a greater accuracy. What is more, they proposed several technically and economically based solutions for energy consumption reduction. Energy Advice professionals have the required competences to conduct energy appraisal activities.
We note that Energy Advice, incl. 303038190, duly fulfilled the contract for the provision of reliability and consumption efficiency audit services of the electrical equipment of the Southern Boiler House electrical power plant of Šiaulių energija AB, signed on 27-02-2014. During the provision of services, a detailed analysis of electrical equipment was performed and conclusions and suggestions were provided on how to achieve greater reliability and consumption efficiency of electrical equipment by making minimal changes to the equipment. Energy Advice has established itself as a responsible company with qualified and honest employees.
Closed joint-stock company Multimeda, company code 147863452, registered at M. Mažvydo str. 12E, Radviliškis purchased an energy audit service from UAB Energy Advice. We note that the audit performed by UAB Energy Advice was performed in detail: compressed air and exhaust ventilation systems, the main consumers of electricity and heat were analyzed, and recommendations were provided. Specialized software has been applied to perform ventilation system flow calculations. The company’s specialists presented the results and answered our questions.
Closed joint-stock company Baldai Jums, company code 156667584, registered at Fabriko str. 3, LT-55111, Jonava purchased an energy consumption audit service from UAB Energy Advice. We note that the audit performed by UAB Energy Advice was performed in detail: the consumption of compressed air and exhaust ventilation systems, electricity, heat and water was analyzed, and recommendations were provided. A solution has been proposed to reduce heat energy consumption in wood dryers. The company’s specialists presented the results and answered our questions.
Energy Advice professionally performed energy audits of equipment and technological processes. During the audit, the consumption of heat and electricity for space heating, ventilation, conditioning and technological process was assessed. Separated energy costs by type of activity: production, administration. The payback possibilities of soft starters have been assessed. An analysis of energy saving possibilities and recommendations is presented.
UAB Energy Advice performed energy consumption audits in three factories of AB MV GROUP Production: Stumbras, Alita and Anykščių Vynas. UAB Energy Advice has thoroughly assessed all possible measures to increase the energy efficiency of these plants. The proposed measures include increasing the efficiency of space heating and ventilation, steam generation and cooling systems. The audit identified waste energy sources and their use possibilities, provided comments on the shortcomings of contracts with energy suppliers. The auditors not only provided conclusions on cost reductions, but also assisted in the adoption of newly installed refrigeration systems, pointing out their shortcomings. We recommend UAB Energy Advice as a responsible partner.
UAB Diab is a leading manufacturer of composite blanks. In order to increase the energy efficiency of production processes, we chose the company UAB Energy Advice, which performed an audit of the company’s energy consumption. The auditors identified the most energy-intensive processes and suggested reasonable measures to increase the efficiency of these processes. The report includes proposals for increasing the efficiency of dust extraction ventilation, compressed air systems, electricity network, as well as reducing heat loss. The service was performed by the auditors without delay.
Closed joint-stock company Kauno Švara, company code 132616649, registered at Statybininkų str. 3, LT-50124, Kaunas purchased an energy consumption audit service from UAB Energy Advice. We note that the audit performed by UAB Energy Advice was performed in detail: the consumption of production transport fuel, the consumption of compressed air and exhaust ventilation systems, electricity, heat and water were analyzed, and recommendations were provided. Solutions have been proposed to reduce transport costs for heat, water and fuel. The company’s specialists presented the results and answered our questions.
2016 UAB Energy Advice performed a comprehensive energy management of the buildings of the Bank of Lithuania (Gedimino ave. 6, Totorių str. 2, 4 and Žirmūnų str. 151, Vilnius) and of the energy management of the buildings (Gedimino ave. 6 and Totorių ave. 2, 4, Vilnius). (heating, hot water, conditioning) condition assessment: an explanatory single-line diagram of the entire electricity network of each building has been prepared and presented, the condition of heating, hot water, conditioning has been analyzed, the reliability of first category uninterruptible power supplies has been assessed, system readiness factor has been calculated, number of failures , the downtime of the power supply system of the first category of electricity consumers was estimated. The proposed measures for optimizing the electricity and energy sector and recommendations for eliminating the identified shortcomings are reasonable and understandable.
“The Energy Advice team performed the energy audit service responsibly. The employees delved into the specifics of our company’s work and proposed measures to achieve the set energy audit objectives. companies seeking to increase the efficiency of the energy economy. “
The audit performed by UAB Energy Advice was performed in detail: the consumption of production transport fuel, the consumption of compressed air and exhaust ventilation systems, the consumption of electricity, heat and water were analyzed, and recommendations were provided. Solutions for reducing heat and electricity costs have been proposed. The company’s specialists presented the results and answered our questions.
Energy Advice performed a full-scale energy audit of technological processes in UAB Gealan Baltic in accordance with the LST EN 16247 standard and the laws of the Republic of Lithuania. After performing the calculations, the efficiency coefficients of the operated equipment were determined and efficiency improvement measures were proposed. The presented proposals are not of a general nature, but have been made after studying the specifics of our company and the principles of operation of production lines. All the proposals presented in the report are economically justified and do not require large investments. The work report, by agreement, is in English. We recommend Energy Advice energy audit services to companies that aim to increase energy efficiency.
“Energy Advice performed an energy audit in June-August of this year. The services were performed professionally and qualitatively according to the pre-agreed scope of services. We appreciate that the measures proposed in the audit conclusions are realistic, technically and financially sound and understandable. the origin of the results obtained and their validity and reliability. We intend to implement the proposed austerity measures in the near future. “
AB Achema is the largest producer of nitrogen fertilizers and other industrial chemical products in the country and the largest such plant in the Baltic States. We note that the company Energy Advice performed an energy audit of AB Achema plant. The proposals submitted by the auditors are focused on increasing the energy efficiency of the plant, the technological units with the greatest potential for savings are indicated. Depending on the specifics of the plant, the report makes suggestions on how to use waste energy resources. The energy audit service was performed in a timely and high quality manner
Energy Advice performed an energy audit service and proved to be a reliable partner. UAB Fazer Lietuva has received professional recommendations for reducing electricity and heat consumption, which can be implemented by making small investments. The company plans to implement the proposed recommendations in the near future. UAB Fazer Lietuva recommends Energy Advice services to companies seeking to increase energy efficiency and reduce energy consumption costs. UAB Fazer Lietuva is a part of the Fazer Group with 15 thousand. employees and operating in eight countries.
UAB AD Wood purchased an energy consumption audit service from UAB Energy Advice. We note that the audit performed by UAB “Energy Advice” was performed in detail: the consumption of compressed air and exhaust ventilation system, electricity, heat and water was analyzed, and recommendations were provided. Solutions for electricity, water, compressed air, heat, cost reduction have been proposed. The company’s specialists presented the results and answered our questions.
The engineering staff of UAB DS Smith Packaging Lithuania participates in practical trainings organized by UAB Energy Advice with the program EA-PSM Electric. We are glad that the acquired knowledge helps to optimize the operation of the electricity network in the factory, downtime and reduce electricity consumption. We recommend UAB Energy Advice as a responsible and reliable partner.
We are glad to have chosen Energy Advice to perform an energy audit of UAB MESTILLA biodiesel plant. The auditors performed a detailed analysis of historical energy and technological parameters and indicators and proposed cost-effective energy saving measures. The audit assessed the efficiency of pumps, heat exchangers and key technological processes and proposed specific ways to increase efficiency. Also, the compressed air production system and the company’s electricity economy were analyzed. We recommend Energy Advice to other companies seeking energy efficiency.
UAB Energy Advice repeatedly performed an energy consumption audit in UAB Fazer Lietuva. After analyzing the engineering systems, a report is presented on energy and cost reduction measures for water, compressed air, reactive power, refrigeration-ventilation and air conditioning systems. We plan to implement the recommendations in the near future. UAB Energy Advice specialists provided services on time and presented the results to the responsible employees. We are satisfied with the services provided.
By order of the Public Limited Liability Company ORLEN Lietuva, UAB Energy Advice in 2019. December. prepared a training program and conducted trainings for the employees of AB ORLEN Lietuva on the topic “Challenges of connection and operation of solar power plants”. We would describe the trainings organized by UAB Energy Advice as professional and effective, as the quality of the trainings always meets the expectations of the Company’s employees. The staff highly appreciated the lecturer Mantas Kaminickas, his professionalism and knowledge of the topic taught. UAB “Energy Advice” services met the company’s expectations and we hope for successful cooperation in the future.
Employees of the technical staff of AB Rokiškio sūris participated in the trainings of UAB Energy Advice “Increasing the work efficiency of compressed air systems in industrial enterprises” and “Increasing the energy efficiency of refrigeration machines”. During the training, employees were reminded of the basic principles of system operation, laws and calculation methodologies, practical examples and tasks were provided. The training left a very good impression due to the lecturer’s competence and professionalism, the optimal balance of the theoretical and practical part of the training, the modernity of the topics and its direct application in practice.
We provide high quality, value-adding services.